Wellington, FL Heating and Air Conditioning
for Wellington, FL
Air conditioning system continuously freezing up; removed and clean evaporator coil, primary drain pan, blower assembly and heater. We Cleaned inside of air handler and disinfect with anti-microbial spray. Cleaned condenser coil, drain line and perform full system check up.
Air conditioning system not cooling; found drain pan filled with water and shut down on float switch. We emptied out drain pan and cleaned the condensate pump and took off and cleaned the trap on the drain line. All operations working properly again.
Completed a Tune Up on customers air conditioner system which includes 23 point inspection, cleaned evaporator & condenser coil, flushed the drain line and cleaned the drain pan. We recommended doing this service twice a year to keep your system running efficiently all year round!